Bosch Rexroth AG
Repeater control signal
Do not short-circuit the output.
Do not exceed the maximum current.
The PROFIBUS connectors each have a connectable terminating resistor.
The terminating resistor must always be active at both the first and last bus
node. Carry out the connection as shown in the figures below.
Bus connection and switch position for first node and last node
Bus connection and switch position for all other nodes
Preparing a cable for connecting a bus connector
To assemble the bus cable, proceed as follows:
Use cable according to DIN EN50170 / 2 edition 1996
Strip cable (see figure above)
Insert both cores into screw terminal block
Sytronix SvP 7020 PFC Variable-Speed Pump Drives
+5 V (±10%)
Max. 75 mA
Output resistance: 350R
≤ 0.8 V at I
≤ 2 mA
≥ 3.5 V at I
≤ 1 mA
Danger of destroying output
"+5V repeater supply" by overload!