Application and circuit for mosfet driver ic (15 pages)
Summary of Contents for Toshiba MBSWH-150-F3-KK
(All cabinets are ANSI-61 Gray (Munsell No. 8.3G 6.10/0.54.)) Part Number* Dim. W x D x H (in) Wt (lb) UPS kVA Voltage Breaker Size Withstand kAIC MBSWH-150-F3-KK 30.1 x 10.8 x 42.1 208/120V 65,000 MBSWH-250-F3-KK 30.1 x 10.8 x 42.1 208/120V 100A...
WARNING AREA TEXT COLOR: ANSI WHITE TEXT AREA BACKGROUND COLOR: ANSI WHITE any of the labels. If the labels are damaged or if additional labels are required, contact your TOSHIBA representative for TEXT AREA TEXT COLOR: ANSI BLACK additional labels.
This manual contains important instructions that should be followed during the installation, maintenance, and operation of WLM 3-9-11 ZIR 3-10-11 WLM 3-10-11 FULL THIS MATERIAL IS THE EXCLUSIVE PROPERTY OF TOSHIBA INTERNATIONAL GENERAL - MBS the MBS to assure safe and proper operation. CORPORATION AND SHALL NOT BE REPRODUCED, USED, OR DISCLOSED REV: TO OTHERS UNLESS PRIOR WRITTEN AUTHORIZATION IS OBTAINED.
MOUNTING INSTRUCTIONS The Toshiba wall-mounted Maintenance Bypass cabinet comes fully assembled. The units are equipped with two lifting eyes each on the top and bottom of the cabinet. Inside on the back panel are four keyholes sized for 1/2” mounting bolts See the appropriate draw- (customer supplied) that are for mounting the unit to cement wall or metal channel support.
Ilsco P/N Description Hole Hole Conductor Fitting Color Diameter Spacing Size CLND-3/0-12-134 Long Barrel 3/8 in. 1.75 in. Orange CLND-4/0-38-134 Long Barrel 3/8 in. 1.75 in. Purple CSWD -4/0-38-134 Short Barrel CLND-250-38-134 Long Barrel 3/8 in. 1.75 in. Yellow CSWD -250-38-134 Short Barrel CLND-350-38-134 Long Barrel...
Connect the power cables as indicated below. Verify phasing is correct before applying power. LINE IN UPS OUT Phase A B C Phase A B C Phase A B C Phase A B C UPS IN LOAD IN Figure 1 - MBS Power Cabling Connections MBS (Wallmount) Installation - 64523-009...
SKRU Wiring If the Wall Mount MBS is equipped with a SKRU (Solenoid Key Release Unit) it comes with the SKRU factory-wired to the MBS Terminal Strip TB-1. TB-1 is mounted on the lower left side of the MBS. Complete wiring the MBS TB-1 SKRU to the UPS dry contacts TB before energizing the MBS or UPS. The SKRU is pow- ered from the load side of the MBS output breaker.
KEYED MECHANICAL INTERLOCK OPERATION The MBS ships with a keyed mechanical interlock or SKRU (Solenoid Key Release Unit) interlock. Operation instructions for both models are shown below, and also displayed on the MBS breaker panel. NOTICE: Both MBS procedures are make-before-break. Ensure the UPS is in BYPASS mode before switching to Maintenance Bypass.
Appendix A - Lock-Out/Tag-Out Hasp Installation The Toshiba wall-mounted MBS ships with a LOTO (Lock-Out/Tag-Out) hasp to be installed by the User in those applica- tions requiring that capability. Installation equipment required: #2 Phillips Screwdriver 1. Twist the inner tongue and outer loop sections of the hasp in opposite directions, until the 0.5 mm join separates.
SOCIAL INFRASTRUCTURE SYSTEMS GROUP POWER ELECTRONICS DIVISION 13131 West Little York Road, Houston, Texas 77041-9990 Tel (713) 466-0277 Fax. (713) 466-8773 US (855) 803-7087 Canada (800) 872-2192 https://www.toshiba.com/tic/industrial/uninterruptible-power-systems Printed in the U.S.A.